Maintenance and maintenance of the boiler!
,经常检查炉膛和烟道耐火砖墙、炉门、看火孔、出灰门、省煤器的管端是否漏风，若发现漏风，应及时嵌缝修补。 Boiler grate , often check the furnace and flue refractory brick wall, furnace door, fire hole, ash door, economizer pipe end for leaks, if leaks are found, timely caulking repair.
,垃圾在第一级炉排上的停留时间应在100～110秒之间比较合适，为了让垃圾在炉内充分焚烧，第二、三级炉排停留时间一般应在80～100秒之间比较合适， 十字刮板 ,为使垃圾完全烧透，第四级炉排的停留时间应在180～200秒之间比较合适。 After the author's summary of more than one year of production experience, the result is obtained: In order to allow the garbage to be fully dried in the furnace, Shandong Boiler Parts Factory , the residence time of the garbage on the first-level grate should be more suitable between 100 and 110 seconds In order to allow the garbage to be fully incinerated in the furnace, the residence time of the second and third stage grate should generally be between 80 and 100 seconds. The cross scraper , in order to completely burn the garbage, the residence time of the fourth stage grate It should be between 180 and 200 seconds.
,要定期清扫除尘器的积灰，保持除尘器的严密性，及时清除漏气地点，以免破坏除尘器的效率，甚至影响导致除尘器不能正常工作。 The boiler hood should regularly clean up the dust accumulation of the dust collector, maintain the tightness of the dust collector, and timely remove the air leakage place, so as not to damage the efficiency of the dust collector, and even affect the dust collector to work normally.